Combustion Tuning using Safe-Fire TempVision1000 resulted a 1.15% percent fuel saving and 2.43% NOx reduction at Pagbilao Power Station in the Philippines
Safe-fire service team collected burner flame temperature data using TempVision1000 on boiler unit #1 at the Pagbilao Power Station, Philippines. After analysing the temperature data and visualizing the performance of the burners at each level, the team adjusted the secondary air dampers to improve combustion of the burners at the DD level. The tuning resulted a 1.15% percent saving on fuel which could potentially save the plant $800K annually on this boiler.
- Boiler: 2×382 MW, T-fired
- Manufacturer: MHI, Japan
- Coal burners: 20